What do you need to pay attention to before installing HEPA filter?
Before the installation of HEPA filter, the clean room must be comprehensively cleaned and wiped. If there is dust accumulation inside the purified air conditioning system, it should be cleaned and wiped again to meet the cleaning requirements. If thehigh efficiency air filteris installed in the technical interlayer or the suspended ceiling, the technical interlayer or the suspended ceiling should also be comprehensively cleaned and wiped.
2. After the clean room and purified air conditioning system meet the cleaning requirements, the purified air conditioning system must be put into trial operation. After continuous operation for more than 12h, install HEPA filter immediately after cleaning and cleaning the clean room again.
3. The transportation and storage ofHEPA filtersshould be shelved in accordance with the direction of the manufacturer’s signs. Handle with care during transportation to prevent violent vibration and collision.
4, before the installation of HEPA filter, must be unpacked at the installation site for appearance inspection, including filter paper, sealant and frame damage; Whether the side length, diagonal and thickness dimensions meet the requirements; The frame has burrs and rust spots (metal frame); Whether the product certificate, technical performance meets the design requirements. Then leak detection. After inspection and leak detection qualified should be installed immediately. During installation, reasonable allocation should be made according to the resistance of each filter. For unidirectional flow, the difference between the rated resistance of each filter and the average resistance of each filter on the same tuyere or air supply surface should be less than 5%. For HEPA filters with cleanliness level equal to or higher than 100 in clean rooms, leakage detection should be carried out according to the method specified in Appendix VI and I before installation. And meet the requirements set out in Clause 5.4.1.
5. The frame of the HEPA filter should be smooth. The allowable deviation of the flatness of the mounting frame of each HEPA filter is not more than 1mm.
6, the seal between the HEPA filter(HEPA filter manufacturer’s)and the frame using gasket, adhesive, negative pressure seal, liquid tank seal and double ring seal and other methods, must be the packing surface, filter frame surface and the surface of the frame and liquid tank wipe clean.
7. When using the gasket, the thickness of the gasket should not exceed 8mm, and the compression rate is 25% ~ 30%.
8. When using liquid tank sealing, the liquid level in the liquid tank should meet the design requirements, and the joints of the frame should not have seepage phenomenon. When double-ring sealing strip is used, do not block the hole on the ring cavity when pasting the sealing strip; Both double-ring seals and negative pressure seals must keep the negative pressure pipeline unblocked.
9. When installing HEPA filters, the arrow on the outer frame should be consistent with the direction of the air flow. When it is installed vertically, the filter paper crease seam should be perpendicular to the ground.